Adding this "product" to your cart will include Cutting Edge Power disconnecting (defeating) the neutral to ground connection in the Rebel Solar Generator, which converts the solar generator from bonded-neutral to floating-neutral.
Automatic Neutral-to-Ground Connection:
Rebel Solar Generators are equipped with an automatic neutral-to-ground switch. These inverters use an internal relay that automatically connects the AC neutral output to the vehicle/ship’s safety ground in inverter mode and cuts off when it is connected to a qualified external input AC power source. This design avoids the simultaneous existence of two neutral-to-ground connections, thereby avoiding the risk of shock hazard between the vehicle/boat’s neutral and the input AC source’s neutral.
In some installations, this function must be disabled. In order to accommodate to these situations, the automatic neutral-to-ground system can be defeated so the neutral will not be bonded in any operating mode. If you are not sure whether you must disable this function, please refer to your local code requirements and the latest NEC code book.
A floating neutral should always be used for backfeeding a house except if you have a switched-neutral transfer switch that switches over the hots AND THE NEUTRAL (instead of just the hots like most transfer switches).